TRANSFORMER OIL DEGASSING PLANTS (capacity 1000 – 10 000 LPH)
Every company activities of which are related to using of industrial oils share the problem of change or disposal of contaminated oils.
Costs of disposal or changing of oils are frequently very high and need a significant investment. Our equipment offers a practical, proven and economical method to purify the oil and use it again.
High vacuum transformer oil degassifiers produced by GlobeCore Co. are of very big demand by different transformers servicing companies. These units can filtrate oil either with or without heating providing nominal filtration fineness up to 1 micron with solid contaminant content in accordance with Class 9 industrial purity (-/15/12 by ISO 4406).
The listed specifications describe the design manufacture and supply of mobile (trailer type as option) high vacuum oil treatment and filling plant for power transformers, suitable for outdoor use and complete with all necessary control and measuring equipment, as described herein.
Units are produced for different capacities to optimize processing of oils, vacuum treatment and drying of transformers of various sizes. Application of these units for oil equipment maintenance extends equipment life and lowers maintenance costs significantly.
Performance in a single pass through the purifier at a full flow rate shall be as follows:
Water Removal: From 50 ppm down to less than 5 ppm in a single pass and down to 3 ppm after several passes as measured by the ASTM Method D1533
Gas Removal: From fully saturated with air (10 to 12% by volume) down to less than 0.1% by volume as measured by the ASTM Method D-2945
Particulate Matter Removal: 98% of particles over 1μm
Dielectric Strength: Improvement in dielectric strength up to 70 kV.
The manufacturer guarantees normal and stable operation of the Unit if all installation, operation, maintenance, transportation and storage regulations, laid out in this manual, are observed.
Warranty period is 12 monthsfrom date of delivery.
If any manufacturing defects or failure of the Unit or it’s components through manufacturer’s fault are uncovered during warranty period, the user is entitled to make a claim to the manufacturer without disassembling the unit or it’s components. In the course of five days the user draws up a preliminary act and notifies the manufacturer of the defect.
Warranty is void in case of:
- insufficient operation;
- insufficient operation medias;
- Unit design alteration;
- use of defective tools;
- use of non-original spare parts;
- unauthorized alteration of the Unit or its components;
- insufficient servicing and maintenance.